40MVC / 38MVC. 40MVQ / 38MVQ. Service Manual. HighWall Duct Free Split System. Sizes To TABLE OF CONTENTS. PAGE. SAFETY. View and Download Carrier 40MVC product data online. High-Wall Duct Free Split System. 40MVC Air Conditioner pdf manual download. Also for: 38mvc. Manuals and User Guides for CARRIER 40MVC. We have 5 CARRIER 40MVC manuals available for free PDF download: Service Manual, Product Data.
|Published (Last):||9 August 2013|
|PDF File Size:||14.43 Mb|
|ePub File Size:||8.44 Mb|
|Price:||Free* [*Free Regsitration Required]|
Carrier 40MVC Manuals
Installing, starting up, and servicing air- -conditioning equipment These instructions cover the carrisr, start- -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, etc. Carefully remove carrrier mounting plate, which is attached to the back of the indoor unit. Ideal installation locations include: The mounting plate should be located horizontally and level Indoor Unit on the wall.
All minimum spacings shown in Fig.
If the installation location may be exposed to strong winduse a ends until all the connections are made. Check with your Carrier representative to obtain Bend tubing with bending tools to avoid kinks and flat spots. Mount outdoor caerier disconnect. Run power wiring from 4m0vc box to disconnect per NEC and local codes. Remove field wiring cover from unit by loosening screws.
Failure to follow this caution may result in equipment 4. Do not use thermostat wire for any connection between indoor and outdoor units. All connections between indoor and outdoor units must be as shown.
The connections are sensitive to polarity. Run interconnecting piping and wiring from outdoor unit to indoor unit.
Run interconnecting cable through hole in wall outside to inside. Lift indoor unit into position and route piping and drain Do not form a rise.
The deep vacuum method is the most positive way of assuring a system is free of air and Failure to follow this caution may result in equipment liquid water. Conceal the tubing where possible.
Make sure that the drain tube slopes downward along its en- tire length. If possible, display LEDs on both the indoor and outdoor units. The outdoor always check the diagnostic codes displayed on the indoor unit diagnostic display is an LED on the outdoor unit board and is first. Page of 14 Go.
Carrier 40MVC Product Data
Read the entire instruction manual before starting the. Add to my manuals Add. Floor console ductless split 40jvc sizes 09 to 12 26 pages.
High-wall ductless split system sizes to 40 pages. Parts List Aa Aa Fig.
Carrier 40MVC Air Conditioner User Manual
Safety Considerations Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, start- -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, etc. Outdoor Unit Installation If the installation location may be exposed to strong winduse a ends until all the connections are made.
Page 14 Catalog No: This manual also for: Comments to this Manuals Your Name. Enter text from picture: The red light under dif has come on and the unit will not work. How do I fix it. By pressing ‘print’ button carrief will print only current page. To print the manual completely, please, download it.
Don’t show me this message again. Got it, continue to print. Don’t have an account?