E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic Terminal block. E5CN. Basic Type. Analog input. Temperature input. safety standards, refer to your OMRON website. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type (Cat. No. H). E5CN-H. Advanced Digital Temperature Controller (48 x 48 mm). E5CN-H between displaying the status of the Temperature Controller (auto/manual.
|Published (Last):||26 June 2006|
|PDF File Size:||12.37 Mb|
|ePub File Size:||8.48 Mb|
|Price:||Free* [*Free Regsitration Required]|
ON and OFF delays can be set separately for alarms 1, 2, and 3. Function Setting range Unit Advanced Function Setting Level Control output 1 alm1 assignment alm1 The safety precautions that are provided are extremely important to safety.
Table of Contents Add to my manuals Add.
Page Soak time, Wait band adjustment level: Adjustment level To limit the manipulated variable ol-l MV lower limit: Page Program pattern initial setting level: Page initial setting levelStandby sequence reset: When the omrin is turned ON, omrno of the display lights for approximately one second.
The degree of protection is as shown below. Revision History A manual revision code appears as a suffix to the catalog number on the front cover of the manual. Communications function with HBA: Section Using the Transfer Output Page Alarm 2 and 3 hysteresis: Green Outside stable band: The program start must be assigned to an event input.
Set point upper- sl-h limit 3. Setting a negative value produces an overlapping band. The following diagrams show the available outputs and their internal equalizing circuits. Press the O and M keys simultaneously for at least one second to return Operation Level to the operation level.
Connect the power supply. Operating Procedure This procedure executes self-tuning ST. Note Protection cannot be cleared or changed without the password. In manual mode, the change value will be fixed immediately and reflected in the e5cj MV.
OMRON E5CN USER MANUAL Pdf Download.
Section Using the Key Protect Level 5. Calibrating A Voltage Input 1,2, Press the U or D key to set alm1. Page to operation level Alarm 2 to 3 type initial setting level: ST stable st-b range Page Section Performing Manual Control Operating Procedure Use the following procedure to mxnual the manipulated variable in manual mode.
Section Moving to the Advanced Function Setting Level Alarms during SP The operation of alarms during SP ramp operation depends on whether Ramp Operation alarms are set to be based on the ramp set point or the target set point refer to the following diagrams.
The default is 8.
Omron E5CN User Manual
PageAlarm 3 hysteresis: The set point limiter is used omorn prevent the control target from reaching abnormal tem- peratures. Operating Procedure The following example shows how to select C as the temperature unit.
Section Loop Break Alarm 3. This parameter executes robust tuning RT.
This parameter is used to check the manipulated variable for the cooling con- trol output during operation. Displays other than that for switching between Power ON automatic and manual. Heater Current 1 Value Monitor Alarm 1 must be assigned. Page Section Loop Break Alarm 3.
Conventions Used in this Section The MANU indicator will light during manual control. 5ecn Transfer type Default Upper-limit alarm Lower-limit alarm Doing so may occasionally result in electric shock, fire, or malfunction.